Main Article Content
In this paper computational fluid dynamics (CFD) was used for simulation of the indoor climate in a part of a low energy building. The focus of the work was on investigating the computational setup, such as grid size and boundary conditions in order to solve the indoor climate problems in an accurate way. Future work is to model a complete building, with reasonable calculation time and accuracy. A limited number of grid elements and knowledge of boundary settings are therefore essential. An accurate grid edge size of around 0.1 m was enough to predict the climate according to a grid independency study. Different turbulence models were compared with only small differences in the indoor air velocities and temperatures. The models show that radiation between building surfaces has a large impact on the temperature field inside the building, with the largest differences at the floor level. Simplifying the simulations by modelling the radiator as a surface in the outer wall of the room is appropriate for the calculations. The overall indoor climate is finally compared between three different cases for the outdoor air temperature. The results show a good indoor climate for a low energy building all around the year.
This work is licensed under a Creative Commons Attribution-NonCommercial-NoDerivatives 4.0 International License.
Authors retain copyright of the published article and have the right to use the article in the ways permitted to third parties under the - Creative Commons Attribution-NonCommercial-NoDerivs 4.0 International (CC BY-NC-ND) licence. Full bibliographic information (authors, article title, journal title, volume, issue, pages) about the original publication must be provided and a link must be made to the article's DOI.
The authors and third parties who wish use the article in a way not covered by the the -Creative Commons Attribution-NonCommercial-NoDerivs 4.0 International (CC BY-NC-ND) licence must obtain a written consent of the publisher. This license allows others to download the paper and share it with others as long as they credit the journal, but they cannot change it in any way or use it commercially.
Authors grant to the publisher the right to publish the article, to be cited as its original publisher in case of reuse, and to distribute it in all forms and media.
 SCNH. FEBY12: Kravspecifikation för nollenergihus, passivhus och minienergihus – Bostäder (in Swedish) (2012)
 Rohdin, P., Molin, A., Moshfegh, B., Experiences from nine passive houses in Sweden – Indoor thermal environment and energy use, Building and Environment, 71, (2014), pp. 176-185
 Lin Z, Chow T, Wang Q, Fong KF, Chan LS. Validation of CFD Model for Research into Displacement Ventilation, Architectural Science Review 48:4 (2005) pp.305-316
 Allocca C, Chen Q, Glicksman L.R. Design analysis of single-sided natural ventilation, Energy and Buildings 35:8 (2003) pp.785–795
 Zhuang, R., Li, X., Tu, J., CFD study of the effects of furniture layout on indoor air quality under typical office ventilation schemes, BUILD SIMUL 7, (2014) pp. 263–275
 Zhai, Z. J., Zhang, Z., Zhang, W., & Chen, Q. Y.. Evaluation of various turbulence models in predicting airflow and turbulence in enclosed environments by CFD: Part 1—Summary of prevalent turbulence models. Hvac&R Research, 13(6), (2007) pp.853-870.
 Rohdin, P. Moshfegh, B. Numerical Predictions of Indoor Climate in Large Industrial Premises - A Comparison between Different k-ε Models Supported by Field Measurements. Building and Environment 42 (2007) pp.3872-3888.
 Wallentén P. Convective heat transfer coeffcients in a full-scale room with and without furniture, Building and Environment 36: (2001) pp.743–751
 Delaforce SR, Hitchin ER, Watson DMT. Convective Heat Transfer at Internal Surfaces. Building and Environment 28:2 (1993) pp.211-220
 Khalifa A-JN. Natural convective heat transfer coefficient – a review: II. Surfaces in two- and three-dimensional enclosures. Energy Conversion and Management 42: (2001) pp.505-517
 Boverket, BFS 2011:26, BBR 19 in English. Boverket (2011)
 Ansys. ANSYS CFX-14.5 Solver Theory Guide. Ansys,inc (2012)
 Chen Q, Xu W. A zero-equation turbulence model for indoor airflow simulation. Energy and Buildings 28: (1998) pp.137–144
 Stamou A, Katsiris I. Verification of a CFD model for indoor airflow and heat transfer, Building and Environment 41: (2006) pp.1171–1181
 Sørensen DN, Nielsen PV. Quality control of computational fluid dynamics in indoor environments. Indoor Air 13: (2003) pp.2–17
 Persson T. Elbesparing med pelletkaminer och solvärme i direktelvärmda småhus. Licentiate Dissertation, KTH Energiteknik, Stockholm, Sweden, 2004 (in Swedish)
 Celik IB, Ghia U, Roache PJ, Freitas CJ. Procedure for Estimation and Reporting of Uncertainty Due to Discretization in CFD Applications, 2008
 Roache PJ, Perspective: a method for uniform reporting of grid refinement studies. ASME J. Fluids Engng, 116: (1994) 405
 Howarth AT. The prediction of air temperature variations in naturally ventilated rooms with convective heating. BSER&T 6: (1985) 169
 Riederer, P., Thermal Room Modelling adapted to the test of HVAC control systems. Ph. D thesis, Ecole des Mines de Paris, France, 2002